Liquidtight Flexible Nonmetallic Conduit Type LNM-P: This nonmetallic liquidtight conduit is ideally suited for continuous flexing situations. It is often specified in “Power Track” or cable carrier installations and on industrial robots. It does not contain a metal core which could fatigue from repeated flexing or vibration.
CONSTRUCTION: Type LNM-P consists of layered, Type A construction that incorporates a smooth seamless inner core of flexible PVC bonded to a covering of flexible PVC. Between these layers is a woven nylon mesh for added reinforcement. The PVC material is a high-quality, flame-retardant compound that resists oils, mild acids and exposure to sunlight.
APPLICATION: Type LNM-P is intended for installation in accordance with Article 356 of the NEC (ANSI/NFPA-70) for flexible liquidtight nonmetallic conduit (LFNC-A or FNMC-A).
Listed File # E79308 Conforms to Underwriters Laboratories Standard ANSI/UL 1660 type A.
Certified File #LL18858 Conforms to CSA 22.2 No. 227.2 Type A.
Fittings: Fittings for layered conduit are for that conduit only and are so identified by the marking “FNMC-A” or “LFNC-A” for liquidtight flexible nonmetallic conduit Type A. 1/2″ straight examples include:
Tests Include: RoHS and WEEE Compliant
Download the Liquidtight Flexible Nonmetallic Conduit Type LNM-P spec sheet below or call 714.835.6211 for more information.Get a Quote Download Spec Sheet PDF